ok, thanks for the follow-up.
The compressor. But i found the problem. The yellow wire and a light blue wire loss connection with one another.
Thank you for responding though.
Can you send me a picture of the wiring schematic or ladder diagram? I'll tell you how to wire it.
what does the contactor control? fan or compressor...
control voltage should be around 24 volts. did you take the old one to match the new one
bought new capacitors and new contactor and new fuse for thermestate and contactor still wont engage by itself. If i push it manually it does come on
I am replacing a sliding glass door and a garden window (both S facing) on my home and have received two slightly differing opinions from two installers
Okay, got the skinny here, one of the outlets in the chain had reveresed Power and Neutral that I corrected. On that same outlet the ground wire had no
Those numbers are from Honeywell Corp.
The R718B and the R7284 are primary oil burner igniter and flame monitoring relay.
Type in either
Hey all, I have an Airease oil furnace with Becett guts. We had it serviced and the tech said the igniter wasn't supposed to be making all those clicking